AC500 Start PLC After stop from Watchdog
For my project ı am using pm573 which communicate with two other pm573's and Scada with Modbus TCP. Sometimes PLC stops from watchdog, so ı configure it from Control Builder Plus to warmstart as it stops from Watchdog(E2 failure). It solves my problem(by use of retain variables).
But ı wonder that, how can ı start program after it stops from watchdog(not use warmstart!).
I Also know that if ı increase watchdog timer sensitivty it stops after sensitivity times of watchdog expire occurs, yet ı do not want to use that solution
I am using CB+ 2.2.0
(CB+ 2.2.0 version's Modbus TCP library have problems?, I also think if it solves my problem to upgrade to version 2.3.0)
Thanks for help
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.