MicroSCADA IEC61850 OPC Server problem
i'm working on a substation's MicroSCADA system setup. Currently, i have a problem with the CET. I made the relay configuration and imported it to the opc server. The values are seen at the online diagnostics but they are not changing. Until i open one of the values' online diagnostics tool, that value doesn't appear on the MicroSCADA process display; when i opened the online diagnostics tool the value seem on the process display. Anyone has an idea about solving this problem?
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.