Substation Automation - IEC61850 - Siemens Relays for ABB MicroSCADA
I have a problem with Siemens relays when integrating to MicroSCADA.
First of all I designed substation at ABB PCM600. Voltage levels etc. Then I imported Siemens relays to PCM600 via .icd files as Generic IED. I generated .icd files for Siemens relays at DIGSI-5 and DIGSI-4.
After that I exported the substation via .scd file from PCM600 to IET600 and added OPC servers etc. in here. After that I exported .scd file from IET600.
Finally I imported .scd file to ABB CET(Communication Engineering Tool) and I tried to do online diagnostic. I can comminicate with ABB relays without ptoblem. With Siemens, I can not. When I try to do online diagnostic for Siemens relays, ABB CET shows me Device Status: Suspended, Connection Status: Not connected. But I can send ping to Siemens relays via MSDOS.
How can I solve it?
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.