PM902F Controller Frequently Switchover and Profibus Slaves shows slave not ready
I have Freelance 2013 SP1 and PM902F Redundant Controller. Till now I made below mentioned observations:
1.) If I Start Both Controller Individually as a Stand Alone Controller then All Profibus Slaves remain Healthy, Profibus Line Redundancy Also Healthy, Controller also Healthy.
2,) If I Start Both Controller to Establish Redundancy without Profibus Line Redundancy only Line-A then All Profibus Slaves remain Healthy, Profibus Line - A Also Healthy, Controller Also Synchronised and Redundancy Ok.
3,) If I Start Both Controller to Establish Redundancy with Profibus Line Redundancy Line-A&B then All Profibus Slaves shows frequently Slave not Ready message and when i observed physically Redundant CI840 module then I found that During Slave not Ready Messages CI840 remains in Dual mode only there is no switchover but frequently Rx/Tx LED goes off and after some time Controller also Start SwitchOver Frequently.
4,) Due to above mentioned point 2 and 3 I thought Line-B Cable might be a Problem so I swap Line-A and Line-B Cable. But In that case also observations remain same as Point 1,2,3.
5,) Then Finally I replaced Both Redundant CI930F modules but Situations remains same as point 1,2,3.
6,) I thought might be I have made some config mistakes in Project. So I create new Test Project with all default values and download into controller but situations remains same as points 1,2,3.
I already updated Controller and CI930F Firmwares. Right now I am not able to decide that it's a problem from Hardware side or Software Configurations Side. Please help me to come out from this Situations. Thanks in Advance..
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.