In SV5.0 sp2 rev C, PLC connect integrated with Honeywell opc server all digital signals showing comm bad
In one of our plant 800xa through PLC connect is integrated with Honeywell opc server via standalone rdm installed in our CS servers we can able to browse and read and write all analog signals where in all digital signals showing comm bad then in reading through advddopcclient and matrikon all digital signals reading good values so on changing over the OPC on Honeywell everything becomes normal (digital also starts reading the value).
What may be the reason why soft point server didn't fetch the values( xa 5.0sp2 rev C) any Ru or workaround for this problem
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.