Compact HMI modbus REAL value
I try read/write REAL value to AC500 PLC with Modbus and Compact HMI.
I can not match desimals if register value is MW1000 in PLC and HRA999,REAL. If I try MD1000 and HRA2000,REAL, write is not possible. With MW1000 and HRA999,REAL configuration nuber has some 2 decimal dig error in number 100.00. In HMI is 100.00 and PLC is 100.17. How to get right signal settings to REAL value?
Insert the URL that your highlighted text will link to.
Copy the video's "embed" tag into Embedded Video below.