Has anyone tried using Modbus TCP/IP with starting address 40000 bit 0 in AC9090F?
I am using TopServer to test my modbus communication in AC900F with CBF ver10.1.
I configured modbus TCP/IP slave in CBF.
I was able to send my data using from the TopServer to AC900F using address 400001 and i can read the value in CBF.
But when i tried to send bool with 400001, the data could not be transfered. I have upacked the data from word to Bool in CBF.
Does anyone has ever try this out yet?
Try to send bool with 40001 address because while reading you reduce by one. Hence while writing need to add one into zero. Just yesterday I tried to communicate with one external SOE device over modbus TCP and it has similar addressing. Though I was only reading from that device but add one while writing and it should work.