BACnet for 800xA
Understand 800xA do not support BACnet protocol.
However, if it is really required in a project , what are the options available to make 800xA connected to BACnet devices.
There are several options ...
- A BACNet to OPC server integrated as a third party OPC system.
- A Web Display from the BACNet manager opened on the 800xA operator displays. Web pages can be integrated into 800xA operator graphics.
- A gateway controller that supports BACnet. Any controller that supports BACNet and OPC will work. Really, this is just the same as the first option above.