In AC900F,How do you configure TU951F into CI930F?
I am using Control Builder F 2013 Version 10.1 for my AC900F redundant controller.
I have to 2 CI930F and 2 TU951F have to be configured into the hardware structure.
However, I do not see any option for me to add TU951F when I clock on the CI930F.
My guessing would be I have insert new object from the AC900FR and select one of the following. Does anybody know which one to insert and what is the procedure?
Voted best answer
Yes, you are right there is no option to insert TU951F into hw structure. Because it's a just hardware link from RJ45 to SUB-D 9 pin male connector. Check image below how to use hardware.
So while configuration just add CI930F and use TU951F just as hw link no configuration required. Note that in future no need to use such hw link because improved CI930F hw is coming which can accommodate two sub-D 9 pin connector.
Also note that having on board two connectors on PB master provides line redundancy and you can save cost for using external Y-Link(RLM).