800xA with advant master: AC450 controller object is unable to retrieve system status
We have MP200 controller with System 800xA 5.0 SP2 installed. AC110 controllers are installed for voltage regulator and turbine governor.
MasterPiece 200 (MP200) controllers interfaces with system 800xA via PU410.
Our task is to replace MP200 with AC450 (PM511) and AC110 with AC160 (PM665) and upgrade 800xA 5.0 to 5.1.
We have installed 800xA 5.1 with all required packages.
RTA board from control structure shows healthy status and services are all healthy.
It is possible to upload through MB300 uploader and all objects are appearing in the control structure but the values are not updating online (Comes with a red cross mark in system status viewer). Controller object shows unable to retrieve system status error.
Faceplate of all uploaded objects are also showing cross marks.
You are not being clear about which part of your project is having problems. I assume you are trying to connect a new AC450 and AC160 to a new 800xA System and that you have uploaded from the AC450 ? ( The AC160 does not use MB300 and the MP200 and AC110 are being replaced so talking about these things is irelevant I guess ? )
The AC450 Uploader and the AC50 OPC server are different things. But both rely on the correct operation of the PU410, the MB300 network and the AC450. So this should eliminate problems with those parts of your system. This means your problem is most likely with the OPC service and setup in your connectivity servers...
- Firstly, I assume you are doing this development on a completely seprate MB300 network and that the new and old systems are completely isolated from each other.
- Is the AC450 in run mode (P1) ?
- Is the OPC service group properly configured in the Service structure ?
- Is the data source for the MB300 Network properly set in the control structure ?