CI867 modbus slave error code -7006
Hello, I have setup my configuration as per the link http://www402.abbext.com/AC-800M-Modbus-TCP-IP-Configuration-SV-5-1_1-0_a4333.a
spx. The MBTCPWrite block produces a -7006 error, "no response from slave". I am not using a gateway, my slave is connected to channel 1 (100 mbps). I have a third party modbus master and want to read data from 800xA. I searched the knowledge store but did not find an answer. I hope someone can help and provide a possible solution. Thank you in advance for any replies.
Voted best answer
You write you have a third party modbus master and the error is "no response from slave" sounds like you have two masters connected together. But in another sentence you write that you have a slave connected, with a slave it could be that the slave has a unitid see the attachement which is taken from the Control builder help file.