When i enter commands same LV, LTREE,... in ON-LINE Builder this message appears:"TRANSLATOR BUSY" .how can solve
on my job used ABB OCS System with Advant Master Software.Controller used in this control system is AC450.when i connect to on of nodes by on-line Builder(v 3.0/0) and enter some commands same LV, LTREE, .... this message appears: " TRANSLATOR BUSY"
Please help me that i solve this problem.
The problem is likely due to a corrupted connection between two PC-elements.
A temporary workaround may be to restart a task on the RTA/OnLine Builder:
# SLLEV SYST
* ACT DAYIP10
# SLLEV PC
However, its likely that the task will crash again once you view or work the corrupted connection.
A corrupted connection can not be listed nor deleted. Normally not even the PC element having the corrupted connection can be deleted.
However, you can delete the whole PC-program after dumping it into source code.
The dump will abort at the corrupt connection(s), but you can start dumping AFTER the corrupted connection and then merge the code back to one piece again before translating it back into the controller.
Having access to a program listing of the code BEFORE the corruption happened will be very useful since you will not be able to dump/see the elements that got corrupted and was "lost".
I recommend that you contact your regional ABB support center in case you need further assistance with resolving this problem.