Ethernet communication AC800F with AC700F
Frelance is 9.2.
Is it possible to realize direct communication via Ethernet between AC800F and AC 700F?
Also between 2 diffrent Freelance Projects?
Other possibility than send and receive?
If yes how?
If not 9.2 with Freelance 13?
Thanks for your hints
Voted best answer
Answers to your question,
Q:In Freelance 9.2, Is it possible to realize direct communication via Ethernet between AC800F and AC 700F?
A: Yes and No,
Yes : via OPC and get communicated over ethernet.
No : Ethernet S/R not supported on AC 700F. In V9.1 & V9.2
Q:Also between 2 diffrent Freelance Projects?
A :Question is little open, But I understood this way, between 2 different freelance projects means between two different controllers. you can use either OPC(fast) or Modbus rtu(slow). This is incase of V 9.2
Q:Other possibility than send and receive? If yes how? If not 9.2 with Freelance 13?
A:This is very good question :), Use Freelance version 2013, Get communicated between AC 800F and AC 700F over Ethernet S/R, Modbus TCP/IP, MODBUS RTU or OPC. Just need to upgrade firmware of existing controller for usage of V 2013.
Just for info, Inside one projects between different controllers get communicated using Exprted(global) variable.
Hope it helps.