CI867 communication error
On slave, even if it is configure as slave I'd 5 the ci867 is looking for slave 255 (FF).
I could not figure out.. great if you can help.
The query from CI867 is in the attached.
Modbus read error is 7006
Thanks in advance
Yes, this is how Modbus TCP/IP is working you find the correct Modbus slave on the IP adress and not on the Modbus ID
If you want to select a specific Modbus ID, then add a Gateway in the Control Builder tree and then under this you and the Modbus TCP/IP slave on position 5.
Now the controller will send Modbus message to ID5