I have faced issue while I started up the master views in power plant .
the master view has connected with connectivity server and aspect server with AC450 by 800xA
System . So the problem is there is no communication between the AC450 And the servers which used as master view . Pless see the attached screen shots and kindly help for solve the problem.
Voted best answer
I assume you by "Master View" relate to Operator Workplace Client of System 800xA?
Is this version 5.1? If so, call the RNRP Monitor (icon with [R] in System Tray) and verify that clients sees servers and/or vice versa. The System Notification icon will not indicate "Connected to System" until RNRP report "node up".
Common issues preventing RNRP from going live between clients and servers:
1) Firewall is enabled, but no exclusions are made.
2) Network switch having IGMP enabled (eg Cisco with factory default settings).
3) Lack of explicit RNRP adressing configuration where so required.
4) Improper network configuration ("routed" L3 instead of "flat" L2 access between client and server).
Client and server must also share the same workgroup or domain, and use the same service account (with administrative permission granted).
I suggest asking regional ABB support team for assistance.