One of our Clients has a ABB 800xA 5.0 System. They have a seperate SCADA System of "IEC60870-5-103" Relay devices,
Which they want to replace with ABB Solutions.
Please suggest possible way to procede for this?.
Details i have attached.
Email me the Possibe solutions or contact details for IEC60870 Support from Austria to my email id Mokshith.email@example.com
For this issue, We have found one cost effective Solution by using some third party IEC103 converter to Profibus DP and taking the data via Ci854 which we feel more cost effective than CI864.
You have to keep the baudrate as high as possible as these converters supports upto 12MBPS.
Any better solutions i would like you get if you guys have any.