AS like question(Please see the link as belows)
We already check Time sync and RTA and Controller Setting.
And We attached System message as your advice.
Please, refet to attached file.
Interpretation (and sources; documents available for download on ABB Library - user account required)
DAXI002 22 9 = Overload in PC-interpreter C
DAXI002 22 10 = Channel to MOTCON handler filled. Overload in system or an aborted handler.
Source: ABB Master System Messages mtype 21, 22 and 132, 5766392-20
CXAA000 30 23 = Addressed DSD, MVI_DSD or TSD not found
Source: CX System Messages & Halt Error Codes, 3BSE000331/B
1) Please seek reason for overload reported by PC-interpreter C and resolve the cause for the overload.
2) Get DataSet, MVI or TextSet error corrected.