IEC 61850 engineering: Problems when importing a scd file from IET600 in 800xa
Nobody answered my last question, so i try again.
If you want a further explanation or the scd file, then just ask.
I am working with IEC 61850 engineering, but have some problems when importing the scd file from IET600 into 800xa. When uploading, using the IEC61850 uploader in 800xa, it comes with a warning saying: “Warning: LN from Other OPC Server present in conducting equipment: AA1\H1\Q02”. As you can see in the attached screen dump, this happens for all the conducting equipment in bay number two.
The structure consists of one substation with one voltage level, and two bay’s with some conducting equipment. The two bay’s have each two relays, a REF630 relay, where some of its logical nodes are placed under the conducting equipment, and a RED615 relay.
For me it looks like the nodes from the second REF630 relay in bay number 2, can’t be imported, because nodes with the same name, but from another REF630 relay, already are placed in the conducting equipment in bay number one. But shouldn’t the relay name have influence on the LN names, so the same nodes from two different relays have different names?
If somebody has some ideas to solve this problem, please let me know.