Add new comment
If power and CEX bus connection is ok! Than check for module itself is tighten properly to baseplate? There is bolt in middle of module, is it screwed properly to baseplate?
You can check in web interface of CI854, typeing IP address of CI in web browser in same network PC, the default uid and pass is service,ac800m respectiviley, you can check for general status or error memory. Advised not to perform this in running plant condition or take experts help in doing so.
Power supply is Ok?,
conection with CPU is OK?