Configuration of Profibus PA transmitter
I want to configure profibus PA devices of siemens make & E & H make. I have imported OT file of both the make through ABB Device Library wizard.
am facing two different issues for both the make.
1. Siemens Make :
We are using siemens make Profibus PA pressure transmitter (Sitrans P DSIII) Model no. 7MF4034. Architecture of our PA transmitter is attached herewith. While communicating with two nos of same transmitter communication shows healthy for one transmitter while it shows unhealthy for other transmitter. Also at the same time
while viewing it in control structure i am able to get access for both the transmitter. While viewing device parameter through control structure i can see software revision is different for both the transmitter althogh model no is same. Screenshot for the same is attached herewith (Name of the file is PA device communication). Please let me know what can be done to make the communication healthy for the other transmitter.
2. Endress & Hauser Make:
While installing DTM library of E & H make it gives error. Screenshot for the same is attached herewith. Please help which file i need to install to make the communicating with E & H transmitter & from where i will get this file.
1. For slave no. 42 take a screen shot of slave diagnostic page from CI854 webserver. Also take a screen shot of a slave that is communicating.
2. For E+H DTM just uninstall the whole DTM completely and install it manually. It will take longer to debug than to install it fresh. At the same time log a support case so that Device Intergration Center is aware of the issue.