How to configured Siemens IED report CET OPC Server Redundance
I would like to configured Siemens IED report 2 CET OPC Server. I configured separated RCB data for each OPC (RCB1 for OPC1 RCB2 for OPC2) but it didn't work. CET OPC Server could connected only one side. (If IED connected OPC1 ok OPC2 not connnected, If IED conected OPC2 ok OPC1 not connected)
How to configured Siemens IED for report 2 OPC ?
The process that you are following is correct. I believe siemens IED will be communicating to siemens scada, so it will report to siemens scada first and then in CET. while generating the scd from IECstation, it will automatically will have some report identity, do not change that. In CET add one more client to report to ABB scada.
I have tried this, it works.
By default SIemens RCB can connect to maximum only 1 client. Hence whichever CET connects to it first it stays connected.
Simple way to circumvent this issue is to create 2 RCB for each dataset. In CET side map OPC1 as client to first RCB and OPC2 as client to second RCB.