Workplace showing different indication for the same objet
I am facing some issues with Operator Workplace.
The system is a 800xA 5.1 Sytem, the system is using ReUsed based graphics. I have two Operators (Op1 & OP2) configured and two sets of system workplace (WP1 & WP2). OP1 is configured to use WP1 and OP2 to use WP2.
The issue what I am facing is that on WP1 I am having the Valves Red=close and Green=Open, when I open the WP2 I get the graphics inverted i.e Green=Close and Red=Open. I am not quite sure which aspect under Workplace object decides what color the object needs to show on different states.
I was wondering if some one had seen something similar to this one before.If so couldyou please guide me.
Thanks in advance
Voted best answer
I did find the solution around, navigated to the Workplace and compared the Reuse Process Color aspect and checked the Logical Color name and correspoding colors for WP1 the ColReuseproValveclose was set to Red where as in WP2 it was set to Green.
This is were the settings are configured for the colors.