Sir how to read holding registers through MBTCP ,here no CI867
The PLC Connect Modbus TCP/IP driver can only work as a master.
To configure it you first create a controller object with the Modbus TCP/IP driver, where you can set the IP address, port and the Modbus ID of the slave. Search the PLC Connect help for Modbus and you will find the addressing supported. You can use C1 - C8192, I1001-I9192 & I10001-I18192, HR4001-HR13999 & HR40001-HR49999, IR3001-IR12999 & IR30001-IR39999, CA0-CA65535 & HRA0-HRA65535. Using the HRA addressing you can also read 32-bit signed integers and floating point reals.
Hope it helps you.