How Generate Digital Output from PP-825 and get input in AC 800 Controller Application
OK, so you mean a Process Panel.. PP-825
Well, it depends what library objects you are using to control your motor connected to the pump, but most of the standard motor and valve objects have a "Panel" mode. You can connect Access Variables to the "Panel" connections for the motor object. The Process Panel can read/write to the Access variables using MMS
If you are using some other library or writing your own motor objects, then you should look at the standard process objects library to see how Panel mode works.