simulate process display using softcontroller
No attachment found?
1) Have you installed & configured the AC800 OPC Server and connected the SoftController to it?
If you are running the SoftController in the same PC as the 800xA's HMI use the address "127.0.0.1:2" otherwise use the remote SoftController PC's IP address + a ":2" suffix, e.g "172.16.4.21:2".
2) You must then configure a OPC DA Connector service group as desribed in the Configuration User's Guide.
In short; on Control Network object; select the OPC Data Source Definition aspect, click "New..." and select the computer running the AC800 OPC Server (from previous step) then select the "ABB.AC800MC_OpcDaServer.3" program ID.
Verify that the newly created service group & provider reaches "Service" state.