PM 783 - DPD22-FBP-DC 705 - problem
Voted best answer
PROFIBUS is working. I had wrong PDP22-FBP cable. When i change it for other, it working.
Thanks for your help.
I have next problem. I have on PROFIBUS CD722 F, because i have to read fast DI , 125 Hz. I was trying to configure this card but nothing.
Can you help me, how i can configure it .
Thanks very much
From image it apperas there is paramter error on slave and also it says staion not ready ! is there anything changed and not loaded ? if it's testing purpose and no harm in making whole station download make whole station download once.
Also check that profibus node hw configuration matches with software configuration ? anything changed on slave parametermask(PROFI_S_Slave) except slave address ?
Not sure alone DC 705 will work or you need to connect atleast one module with DC 705 ! Can't remember exactly but if you have one remote module try to connect after DC 705 and load the configuration.
Perform SCAN bus at profibus master i.e at 2nd image attached in answer above at master image. Right click >scan bus. if it scans bus address 8 then master is able to access slave address 8 but there is some error in slave configuration or parameterisation.