how to reset hours and start counter of gas turbine in 800xA based on MP200?
We have MP200 as main controller for the control system of gas turbine , its "no of start" and "service hour counter shwoing zero , how to rest these counter to get actual value of "no of start" and "service hours", kindly help me
I would ask the person or company that provided you with the graphic display.
You could also backtrack to what Advant/Master controller objects these display elements derive their information from and attempt to update the information there. Possibly you can use the 800xA HMI, but maybe you need to access the data via MDB commands in the Control Builder A tool, etc.
In any doubts, please contact the vendor of this display.
Open the display where you have for instance the number of starts. Click on the number of starts and this should open a faceplate. On the face place you can select the button "Block", a new window will appear under. You can write the number of starts as reported by the analogue physical counter. It will be the same preocedure for service hours and other operation counters. Please note that everytime you reboot the Operator Station all counters will go to zero and you will have to redo this process for very digital counter.