totalizer saving after whole station download
after i download whole station i lost all the totalizer have made befoe
there is any soluation to keep counter data even you do whole station download
Voted best answer
Seems it's related to freelance AC 7/8/900F controller.
Note that it's also possible to load the changes via 'Change Object' where it performs incremental download and ongoing computing not get disturbed. Only if required perform whole station download in case of running controller if it's inhouse activity it's fine else note that whole station download stops controller for a while as well performs cold start before start hence variables start with initial values if defined. in summary after whole station download not possible to save/hold previous values as it's fresh start for a controller.
Hope that helps!
you are using the standard totalizer from some ABB standard library i.e pulp&paper,Minerals etc or you make it by yourself.
Please share the word doucmentation of your totalizer i will check that if there is anything which you miss.