AC500-eco PM554-eth have error ( 26 ) Configuration Data
how can i erase this error ?
Voted best answer
By default the Error light will turn on for even minor errors. Sorting out what error is causing you the problem can be "awkward".
In Control Builder Plus ( not CoDeSys ) right click on the CPU and select "Online". Then click on the CPU to open the Diagnostics error message. Acknowledge all messages and your error light should clear.
You can configure the On-Board I/O, I/O Bus and Ethernet Port Settings to "Run on Config Fault" = "True" so that your PLC program can still go in to "Run" mode even with minor errors. Also search for help on configuring the Error LED to only show E1 and E2 errors. (E3 and E4 errors are less severe and not usually worth showing on the Error LED)
This code shows that you have an error in your configuration. It may be caused by many differen problems. To give you any specific sugestions I need more info. Follow the instruction below:
"If one or several non-acknowledged errors exist, the errors can be displayed and acknowledged according to their occurrence order using the <DIAG> key. Pressing the <DIAG> key the first time displays the error class and error identifier. After this, pressing the <DIAG> key several times browses through the detail information d1=component, d2=device, d3=module and d4=channel. If the "d4" information is displayed and the <DIAG> key is pressed once more, the error class/error identifier is re-displayed.
If you quit the diagnostic display by pressing <ESC>, the error is not acknowledged and displayed again when pressing the <DIAG> key.
If you quit the diagnostic display with the <OK> key, the error is acknowledged.
The LED "ERR" goes off when all errors are acknowledged."
Please follow the above procedure and write down detail infotrmation d1, d2, d3, d4. This four numbers will allow me to give you more specific advice.
Hope it helps.