our system is ac450 with abb800xa5.0
we created a pidcont in ac450 given the name as tic.1.100,we upload the pidcont in the control structure using the mb300 uploader the new piccont tic.1.100 is updated in the control structure ,i just override the grpahic element for the picont in control structure and dynamised in one of the grphic display later i changed the tag number from tic.1.100 to tic.1.200 in the ac450 and uploaded ,edited the graphic display delected the tic.1.100 and tried to deploy the graphic display it not deplayed
in the control structure the tic.1.100 is showing if i manually deleted it is popping alarm like please delete the reference ,
then we restore the graphic display with our latest structure backup now there is no pid control element in the screen,
iam trying to delete the pidcont in the control structure but is showing the msg dependant object exist,please fidn the attached
please help me in this regards
It seems the Aspect is still referenced in the Graphic Display, or at least 800xA thinks its still referenced...
Does it work if you first delete the Graphic Display Aspect which is shown as reference, then delete the Control Module, finally re-import the Display and open Visual Basic? This should then probably give you errors about missing items.
Of course you'll need to have a backup ready just in case...