PM866 has been intentionally stopped
Following fault occured at one of our sites on 23rd september.
F 2016-09-23 23:28:16.054 (local time) 4104 irq err
This PM has been intentionally stopped.
- CPU stall timer has expired (Acknowledged)
- Manual shutdown was requested, error code : 4104
Press init button or remove power to restart...
Kindly let me know whats the reason could be. I have attached the log file.
Voted best answer
If this is with a System Version 5.0 SP2 before Revision C (i didn't check your firmware Versions...) - it could be the bug in issue 800xACON-OL-5020-020.
There is a Field Alert out for this issue as well, but it just says:
A hardware related part of the firmware may execute too long. It will be detected by the built in IRQ supervision mechanism.
No workaround other than updating to a newer Firmware is given.