abbsrvcc800xA.exe*32 processes keeps adding
Version 800xA 5.1 FP4, 64-bit, on VM ESXi 5.1
We have noticed that on ACS1 and ACS2 (but not at the same time)
an extra process with this name is added to the task manager. (See the screendump).
Happens about every 10 minute.
Anybody have an idea what could be the problem?
This process is launched by PROFIBUS/HART OPC server. If P/H OPC server is not configured correctly this process will keep on adding.
If you are not using P/H OPC server then disable the service otherwise run the P/H OPC configuration so that P/H OPC server finds the missing files.
We do not plan to use P/H OPC server. I beleve the thing was needed to be installed because we needed the device library wizard to intall the UMC100 profibus device.
How to disable it the service?
I can see in the contol panel that "ABB Fieldbus Builder Profibus/Hart with OPC server S-FP 126.96.36.199" is installed - I guess uninstalling this would help - but would that also make the device library wizard client and server not working anymore?
ABB Fieldbus Builder Profibus/Hart with OPC server S-FP 188.8.131.52" is a required installation for working with fieldbus devices like UMC100. You should not uninstall it.
To disable the service, go to service structure-> navigate to OPC DA connector and look for which OPC DA connector is configured for P/H OPC server (check for OPC ProgID ***Fieldbus.DA*** ). Uncheck the Enabled check box. This should take away the PH OPC server from service.
Sorry, Can't find it. I guess you mean navigate to the service structure in a engineer workplace in 800xA.
Not sure where to find the ProdID?
But yes using the AdvDsOPCClient.exe tool I do see the Fieldbus.OPCServer is running....
Question is just still how (where) to disable it?