Valve Uni - FB 6 comes up with alarm
I am having same issue like you where I have configured valve uni with Feedback configuration 6 and every time I open valve I get an alarm.
did you get resolution for this problem?
Can you please help?
Voted best answer
I did manage to get this resolved. I had originally copyied an existing Motor block. To resolve I deleted it and added a new instance of the MotorUniM. Just looking at it now my FBConfig = 6 and the object error alarm does not come in when I start / stop the motor. I also have EnableObjErr = true and AEConfig = 1.
Hi, Thank you for your response.
I m having issue with ValveUni block and not MotorUni. I am trying to control valve without feedback therefore I configured FB config to 6 but whenever I open valve, I get an alarm.
In my instance ValveUni block is getting used, does anyone know solution on how to implment valve without feedback using ValveUni block?
Hi, My valve output is connected to Digital output card so whenever I open valve from HMI, it sends 24VDC to valve so actuating that output (Opening Valve). The valve doesnt have any feedback so I configured Feedback configuration to 6 as no feedback in Valve Uni Block but as you said whenever I have my output to 1 and no feedback signals, I get an alarm. I dont want this alarm as my valve doesnt have feedback so I am not expecting any feedback.
How to configured Feedback configuration in using Valve Uni block so I dont get an alarm when my output is 1? I can connect my output to feedback inputs but thats not ideal solution so was looking for better option and wondering why "FB - 6, No Feedback option" doest work with Valve Uni Block.