"AC800M Standard Trend" Template not showing graph
I have conrfigured SignalInRealM objects for all Analog signals in 800xA. In Object Type Structure (for SigRealM object) bydefault "AC800M Standard Trend" template is being used for Trend display. This trend template is instantiated with all 800xA objects in system.
In Control Structure, I have configured Log Configuration aspect for any one of the objects. I am getting values from this log file after defined timeframe but these values are not showing up in by default Trend display (AC800M Standard Trend).
Same Log Configuration file was showing values for newly configured Trend as below;
In control sturcture, I add one Trend aspect and selected "AC800M Advance Trend" as Trend Template. this newly added trend is showing values for configured Log File.
Please guide how to resolve previously configured Trend (AC800M Standard Trend) so that it start showing log values.
Prompt response and guidance shall be highly appreciated.
Does Log Configuration->Status tab->Read return values with good quality?
AC 800M trend template uses the (least desirable) Momentary treatment preventing access to secondary logs. Only primary (raw) logs will be considered by Momentary and ExtMomentary treatments, use TimeAverage to enable any log in selection process.
If this explain the loss of trend, please file an enhancement request with your regional ABB sales representative.