IEC61850 Uploader creates different Objects in Functional Structure
I just started with a new IEC61850 Project Vertical Integration in 800xA, with the Uploader however it creates the Logical Nodes in Functional Structure as new Objects without Connection to the Control Structure - all Logical Nodes are existing twice, while it should be the same Object in both structures. Obviously then i only get "AddItem Error" for all the Properties on the Objects on Functional Structure...
I didn't even come to test the new IED Mapping Functionality in FP4 because all the OPC Properties in Control Connection on the Bay Objects are left with empty Paths.
I tested all possible settings in the Uploader, only possible error i can see is "iec61850OcsPostProc Component does not exist" on "Retrieve Objects" step.
What could be the Reason for this?
Voted best answer
We had the same problem in one of our last projects, when we did the import all the object were created in the fuctional structure instead of control struture. We tried for few days, but then we copied the objects from functional structure to control structure and found that it is working. Please note that in our project the IEDs were RTU560 on IEC61850 protocol.
Cecil Jeeva Dhas