Workplace Screen Problem
I had a client and this client removed and rejoining DC, windows verifyer tools wizard worked and I allow administrator right of operator users. Green icon appeared instead of red padlock. However operator workplace comes with blank alarms comes but mimic diagrams do not come.I chooes everyone member group for this account. How to solve this problem.
Voted best answer
Looks like an installation problem.
DCT Software Compare is recommended!
I also recommend repair/reinstall of the ABB Third Party Common software bundle
There is a MS KB that fixes a .Net issue that PG2 can be in need of. Can't remember the exact number but was 976xxx on XP on Win7 it was superseeded with one having a 1xxxxxx 7-digit number. This KB is "mandatory" but not officially listed in so many places. Will update thread with KB number tomorrow.
Operators do not need administrative permission in Windows nor 800xA.
Minimum group membership typically is:
- Domain Users
- IndustrialITOperator (or whatever group has been associated with the Operators group in 800xA)
I recommend filing a support case with your regional ABB support center.