Can someone please help me, i have a problem with the TCP / IP configuration.
I adjusted the IP and the gateway in windows and in ABB Configuration.
I have a switch with 9 participants. If I want to Load the Projekt an error appears No TCP/IP connection. Could there be another tool too adjust the IP.
Voted best answer
To get connected via CBF to controller online,
Apart from windows IPV4 setting you need to set IP in CBF in network config, and also your engineering station IP at configure tool. check image below for example of cbf and emulator running on same PC.
Controller and CBF should be of in same subnet. by default it is 172.16.1.x (IP), 255.255.255.240(Subnet mask).
Also controller HW IP should match with Network configuration IP of controller.
Find freelance getting started manual @ http://www05.abb.com/global/scot/scot296.nsf/veritydisplay/dccb84483ca27155c125
Hope that helps...