Panel 800 timeout
I have a probleme with my connexion between my controller and the Panel 800.
Sometimes, when I want to change a value on my CPU (from False to TRUE on a digital variable for exemple), the time between the effective change on my CPU and my Panel is 45 secondes !
On digivis, I can see a timeout. But I don't know how to be quicker...
Thanks for your help :)
PS : panel builder 800 and CBF 2013
It is possible you have some data configured in your Master (CBF), that you have not defined in your panel, in this case the master try to read these values but if there are nothing in the panel, master wait for one response in each reading cycle.
Another option is to increase baud rate, it could help.
Thanks for your answer.
I found the solution : on CBF, in hardware, where I declare the slave, I have to check "slow down send cycle". I will inserts a time gap of 10 ms between each message.
But I don't know how to change the baud rate... (it may be useful for after)
Thank you !