Freelance 2016 compatible with OPC UA?
I am planning on using an AC500 PLC with the CoDeSys V3 OPC UA server.
Will the Freelance 2016 software be able to use this OPC UA server?
The answer is: No, it won't.
Freelance Operations and Engineering (Digivis and CBF) have a build in OPC DA and AE clients with OPC tunneling. What You would need is OPC UA client or an OPC DA/AE client with UA Wrapper. So unless You have something like that (I mean UA Wrapper), then it won't work, sorry.
Hope this helps,