error ac800f redundancy
Dear Ms LinHan,
Thanks for your support,
About hardware configuration, i used setting standard with main cpu ip :172.16.1.1 and backup cpu ip 172.16.1.2 ; cable connect between CPUs is cross cable
But i load program for cpu have error no redundancy
please help me!
i send you program and picture system running.
your network configuration matching with real hw setting , check for rotary switch on E2 slot, check image below
It that is fine, then as WeiFeng replied load OS via initialise all or via Configure tool
(All programs > ABB Industrial IT > Freelance V9.x > Configure) you can perform boot EPROM download with both the IP.