Coupling problems PCV02/PCV24 to POC01
A description of this resolution:
- Use POC01 with index 10
The problem is solved by increasing the resistance on POC01. This resultes in a new working point. Therefore the POC01 index will be increased to 10.
On principle, the update must provide for a POC01 from index 10 on if an existing central operator panel shall be used further.
If a defective PCV24 is to be replaced with a new PCV24 or a PCV02 (compatible mode) in V7.2x, a POC01 will also have to be used from index 10.
"Coupling problems PCV02/PCV24 to POC01" resolves the following:
Using the PCV02 (compatible mode) or the PCV24 may cause coupling priblems between the POC01 and the PCV02/PCV24.
- Since with new systems only the compact operator panel is used and as a result no POC01 is employed the above mentioned case may occur only with updates to V8.0x if an existing central operator panel shall be used further. Moreover, the case may occur when a defective PCV02/PCV24 is used in V7.2x.
The underlying cause is:
- Hardware problem