Selecting the phase image from the message line/alarm page is not possible
A description of this resolution:
- Reconfigure the phase control
Selection via DISPO - RECIPE IMAGE - PHASE IMAGE or reconfiguring and storing respective phase control of phase "manual input".
"Selecting the phase image from the message line/alarm page is not possible" resolves the following:
When selecting pending recipe message MANUAL INPUT from the message line/alarm page the phase image cannot be called.
A manual input is requested by a yellow message (I-?). By selecting the recipe message, for instance, from the message line the phase image can be called directly for manual input.
This selection will not work if the image assignment group is missing.
The image assignment group is automatically entered in V7.2.
When duplicating functions from previous versions these assignments may get lost.
The underlying cause is:
- Fault in V7.2D