Scrolling Page and configuration of single graphic displays in V8.0
A description of this resolution:
Configure 'dummy large display' by entering a 'dummy single display' at A/01 (upper left).
Before every graphic display configuration in V8.0C to 8.0E the following handling must be performed:
- Before entry in configuration dialog call 'dummy single display' on monitor (or BA channel respectively) provided for the configuration. Then the configuration dialog of graphic displays can be called on this monitor (or BA channel respectively) without difficulty.
'Scrolling Page and configuration of single graphic displays in V8.0' resolves the following:
Calling a single graphic display entered in an odd column (columns B, D, F, H, K, M, O, Q) on a monitor and subsequently calling the configuration dialog of a single graphic display on the same monitor (or BA channel respectively) will destroy the segment list.
Message SEG. LIST DEFECTIVE appears (immediately with PDG30/31 and in a time-shifted way with PDD02). Immediately after that error message the operator station must be initialized.
With PDD02 several superimposed displays can be represented in the configuration dialog.
The error does not affect display data of the graphic displays in the system list.
The error concerns SW versions 8.0C to 8.0E.
The underlying cause is:
- Software error
Software error in configuration dialog in the case of page scrolling.