Cannot get any data for Loop FCM or Loop Detail displays, but other MOD displays for that same RTDS work fine
- Restart the Loop Server
As the Operate IT service account user, use the Task Manager to end the process ADVLOO~1.EXE and then refresh the Loop FCM or Loop Detail display. You may have to do this on the primary and backup RTDS.
- No data appears on either Loop FCM or Loop Detail displays
Neither the Loop FCM or Loop Detail displays contain dynamic data. Other MOD displays for that same RTDS work fine.
- Loop Server task is not running
This situation generally occurs if either Loop FCM or Loop Detail displays are invoked during a Loop Load (Loop Compile/Install/Download). There may be other conditions which cause the loop server to lock up.