Set technical key Emax 2
I'm trying to set up a IEC61850 based network using Emax 2 breakers and PCM600 software. PCM600 is not able to 'Read from IED' because the technical key does not match. Where can I find the technical key for the emax2? Using the ekip connect software and an usb key I cant find this information or where to define this.
You can 'Read from IED' and use the IED Configuration functionalities of PCM600 only for devices which has a Connectivity Package. Emax 2 don't have a Connectivity Package as far as I know so you can't actually read the configuration out of it.
However you can still use PCM600 to configure IEC61850 communication of Emax 2. Instead of reading from the device, you need to import an Emax 2 .ICD file to PCM600. Then you can change the technical key in PCM600 'Object Properties' and use the IEC 61850 Configuration tool to configure IEC 61850 communication. After configuration you can export an .IID file from PCM600 and write it to the device with Ekip Connect.
So use Ekip Connect to the actual communication towards the device and PCM600 for the IEC 61850 configuration.
The whole configuration procedure is explained in the 'Communication System Interface - Emax 2' -document, which can be found from ABB website. http://new.abb.com/low-voltage/products/circuit-breakers/emax2