Giving problem in calibration instrument from DCS side.800xA
In redundant configuration with 2 Aspect server, 2 connectivity, 1 ES , 5 OS, and 1 IMS server. From few days its giving problem in calibreration of field instrument(profibusPA) through Device management from DCS side. While going online parameterize its not giving further option. How do I resolve this issue? urgent please help.
Please find attached print screen, it will make care idea.
The DTM of TFx12 uses DCOM settings in order to be viewable. Refer to error messages given in the document 3BDD011934-510_B_en_System_800xA_Device_Management_5.1_PROFIBUS_and_HART_Config
Also read the Release note of TFx12 device type. It will tell you which DCOM setting you need to do.
it is bad design on part of DTM to use DCOM, but it is what it is.