Sir i had a panel in which all the Analog Signals are Two wire connection, the Module is AI810 with Base TU810, can some one tell me how to force the MA ( 4-20 MA ) across module to read the values in softwar. The Software which i am using is Freelance 2016 SP1. Can some one help me trigger out this problem.
In Freelance, you can force the inputs/outputs in the parameter dialog of a PROFIBUS device (assuming that the AI 810 is connected via PROFIBUS to Freelance). Go to the force/Sub-tab of the dialog, set the force value, and check the force enable checkbox. Download the changes.