Alarm analysis configuration
Voted best answer
If you have only just created the Alarm Analysis object you might just need to wait. The graphic elements with the red crosses use calculated results based around the reporting period configured in the Alarm Analysis service in the Service Structure, so will need at least the configured reporting period to complete their initial calculations. 3BDS011222, System Configuration, Section 2.2 relating to Alarm Analysis has the following comment...
"When creating a new Alarm Analysis object, a complete reporting period needs to be collected, before any data is presented for that period. In this case the Alarm Analysis display and elements may indicate bad data quality (that is, no initial data) for up to 2 reporting periods. This also occurs when the Alarm Analysis service group is started."
The instantaneous alarm rate data in the control connections screen shot appears to be working so I think its just a matter of time before the other properties come good.
Hope that helps,
Source: 3BDS011222-6*, ABB Ability™ System 800xA System Configuration