Failed to connect to the connectivity server Compact HMI and CCB V6.0.1
I have been working on a project related to Compact HMI + Compact Control Builder V 6.0.1 following the document 3BSE040587-601 _-_ en_Compact_HMI_6.0.1_Getting_Started and the video of this playlist which is on Youtube
At the moment I have managed to configure everything without problem and I got to the point of configuring the OPC server which I have configured without problem and using Softcontroller as seen in the attached image OPC Server Status and SoftController OK
At the same time I have created a simple project in Compact control builder to test that the connectivity is fine and indeed everything is working correctly as seen in the attached image Simulation CCB
Now the problem I am experiencing is when I go to create an object in Engineering Workplace / Control Structure / PLC Connect Servers / OPC Servers / AC800M OPC Server 1
The procedures that I see in the documentation does not comment on how to configure the Connectivity Server, I would like to know if there is any procedure to overcome my problem or what I can review.
I was reviewing another project with Compact HMI + Compact Control Builder and I found that in the Service Structure there is an object called OPCDA (see next image) but I don't know how to configure it. Could you give me information?
Thanks a lot for any information
Voted best answer
please check the Serviceprovider of PLC Network:
Click on Modify and select the connectivity Server, where the AC800M OPC Server is running (normaly the CHMI Server).
BTW the Servicegroup is where you have to look in the ServiceStructure:
I hope this helps