AC800F, no operating system, cant download the program
After the first start-up procedures and initialization in CBF i see inscription "No operating system". When i try to make an initial download or load the whole station, it reaches 100% and inscription is displayed : "the D-PS RSU resource is loading.Connection of communication channels." And nothing else. AC800F goes into "failure" and connection with Ethernet module is lost. What mistakes could I have made? Thanks a lot ..
That is not a normal behavior of AC800F. On what you told, i would say you have done nothing wrong. Usually we do connect, load whole stations, done. So you have to investigate, what's wrong with the controller.
What's the history of that controller? Is this a new one, or a dirty, dusty spare part? Maybe used, replaced because of a failure? Can you access the controller's website? (just open the controller's IP in browser). You can also try a firmware update. Start->...Freelance->Configure->Controller-Firmware-Update->Type in IP->"Load". Do not cut the power to the controller during this update! Maybe this was happen in the past and is the reason for the failure now.